Mns 380V 660V 5000A Best Low
Switch cabinet is through the comprehensive type test, and through the national compulsory product 3C certification. TheSend your inquiry
|The Main Bus Is Rated to Withstand Curre||100ka/1s|
|Maximum Working Current of Main and Bus||5000A|
|Distribution Busbar Working Current||1000A|
|Distribution Busbar Peak Current||102-176ka/0.1s|
|Main Bus Rated Peak Current Tolerance||220ka/0.1s|
|Rated Insulation Voltage||660/1000V|
|Transport Package||Wooden Case|
Switch cabinet is through the comprehensive type test, and through the national compulsory product 3C certification. The product conforms to GB7251.1 "low-voltage switchgear and control equipment", EC60439-1 "low-voltage switchgear and control equipment" and other standards.According to your needs or different occasions of use, the cabinet can be installed in a variety of models and specifications of components;According to different electrical equipment, multiple types of feeding units can be installed in the same column cabinet or the same cabinet.For example: feed circuit and motor control circuit can be mixed together. MNS is a full range of low voltage switchgear to meet your full range of requirements. Suitable for all low pressure systems up to 4000A. MNS can provide a high level of reliability and security.The humanized design strengthens the necessary protection for personal and equipment safety. MNS is a fully assembled structure, and its unique profile structure and connection mode as well as the compatibility of various components can meet the requirements of harsh construction period and power supply continuity.
1. Ambient air temperature: -5~+40 and the average temperature should not exceed +35 in 24h.2. Install and use indoors. Altitude above sea level for operation site should not exceed 2000M.3. Relative humidity should not exceed 50% at max temperature +40. Higher relative humidity is allowed at lower temperature. Ex. 90% at +20. But in view of the temperature change, it is possible that moderate dews will produce casually.4. Installation gradient not exceed 5.5. Install in the places without fierce vibration and shock and the sites insufficient to erode the electrical components.6. Any specific requirement, consult with manufactory.
A corner of the production workshop
Product application case